|Blower Door Testing|
With today’s concerns for energy conservation and carbon footprint reduction, determining the energy efficiency of a building has become an essential cost-containing tool for the building owner. Properly installed insulation is one major contributing component to a building’s performance. Air leakage problems, however, are often overlooked. In many buildings, excessive air leakage is the biggest factor reducing energy-efficient performance.
Wasted energy and high heating and cooling costs are not the only problems caused by air leakage through the building envelope. According to a recent study of US commercial buildings: “...envelope leakage has several potentially negative consequences. These include uncontrolled and unconditioned outdoor air intake, thermal comfort problems, material degradation and moisture problems that can lead to microbial growth and serious indoor air quality problems.”(1)
By placing the building under a known pressure, a Blower Door test allows the technician to measure how much building airflow is required to maintain a certain pressure differential between indoors and outdoors. The number of air changes per hour (the complete replacement of the indoor air volume of the building in one hour) at a standard pressure differential (interior pressure compared to exterior pressure, measured in Pascals) reveals the building envelope's air leakage profile.
Blower Door measurements can also be used to estimate the natural infiltration rate of buildings. While the Blower Door doesn't measure infiltration rates directly, test results can be used along with mathematical models to estimate annual average and design infiltration rates for the purposes of estimating the efficiency of the building envelope, evaluating indoor air quality, estimate the need for mechanical ventilation, and to help with proper sizing of heating and cooling equipment.
A Blower Door consists of powerful variable-speed fan units mounted in an adjustable panel that temporarily fits in a doorway. Pressure gauges connected to the fan measure the rate of airflow required to maintain the building at a certain pressure. This controlled airflow enables the technician to both find and measure air leakage in the building envelope.
A basic Blower Door system includes three components: calibrated fan units, a door-panel system, and a device to measure fan flow and building pressure. The Blower Door fan is temporarily sealed into an exterior doorway using the door-panel system. The fan is used to blow air into or out of the building, which creates a small pressure differential between inside and outside. This pressure imbalance forces air through all holes and penetrations in the building enclosure. By measuring the airflow through the fan and its effect on the air pressure in the building, the Blower Door test measures the air tightness of the entire building envelope.
Scientific studies and practical experience tell us that commercial and institutional buildings often have significant air leakage problems, regardless of their age, size or construction. Blower Door testing, which was originally developed as a research tool for scientists, is now a standardized method for assessing the integrity of the building envelope. It is widely recognized as an efficient and cost-effective tool in the quest to to improve building energy efficiency, reduce carbon emissions, and enhance indoor air quality.
1. Airtightness of Commercial Buildings in the U.S., Emmerich and Persily, National Institute of Standards and Technology, Gaithersburg, MD
|Our technicians and equipment can test your project or facility in compliance with the latest industry standards:|
E 779: Standard Test Method for Determining Air Leakage
Rate by Fan Pressurization.
ASTM C 1060: Standard Practice for Thermography Inspection of Insulation Installations in Envelope Cavities of Framed Buildings.
ASTM E 1186: Standard Practices for Air Leakage Site Detection in Building Envelopes and Air Barrier Systems.
ASTM E 1827: Standard Test Methods for Determining Air tightness of Buildings Using an Orifice Blower Door.
ASTM E 2178: Standard Test Method for Air Permeance of Building Materials.
ISO 6781: Thermal Insulation – Qualitative Detection of Thermal Irregularities in Building Envelopes – Infrared Method First Edition.
US Army Corps of Engineers: Air Leakage Test Protocol for Building Envelopes – Version 3
|Building Envelope Analysis More About Green Building|
|You can improve productivity and occupant
comfort and reduce energy costs at your facility.
Our nondestructive testing pinpoints and prioritizes your heat loss problems.
Save money and conserve energy. Call today for a free quote: 800-879-1964
|Serving the Special Needs of Your Industry:|
|Call Toll Free: 800-879-1964|
|USGBC and related logo is a trademark owned
by the U.S. Green Building Council and is used with permission.
All other content copyright © 2003 - 2014 Infra-red Analyzers, Inc.